Address：Chen Jia River Industrial Park, Mashan East Road, Jimo District, Qingdao City,PR China
Fan maintenance and maintenance measures include:1 、 lubrication system inspectionA. daily check the oil storage in the tank is lower than the low line, such as lack of oil, please refuel.B. daily check oil is mixed with moisture and other dirt and deterioration, such as deterioration, please replace the oil in time.C. daily cleaning oil filter.Oil droplets D. daily check drop nozzle is normal, such as drip nozzle dirty removable adjustment screw cleaning.2. Check the air filter, check whether the air filter is dirty or not. If it is dirty, remove the air filter, unscrew butterfly nut, remove the cover, and clean the filter sponge. (remove the filter, be careful not to drop the dirt into the fan main engine)3, check the triangle belt, fan running for some time, the triangle belt will stretch. At this time, the fixed bolts of the motor are loosened, the motor is moved, the tension triangle is taken to a suitable position, the motor is fixed and the bolt is tightened tightly, and the end face of the motor pulley and the fan pulley is taken to be in the same plane. At the same time, check the tightening screw two pulley is loose.4, often check the fan and motor running condition, if found noise, temperature is not normal, should stop in time to overhaul.5, daily inspection of oil spills, leaks and repair parts, if not repaired, please notify the manufacturer immediately.6. Clean the air conditioning room regularly, keep it clean and well ventilated.7, daily inspection safety valve flexibility, such as not flexible, please wash debugging, to ensure reliable opening and closing.
Copyright Qingdao ShengHeYuan Machinery Co. Ltd. Qingdao ShengHeYuan Machinery Co., Ltd.|Qingdao Aquaculture Equipment|Qingdao Animal Husbandry Fan|Qingdao Fan|Qingdao Negative Pressure FanAddress：Chen Jia River Industrial Park, Mashan East Road, Jimo District, Qingdao City,PR China Telephone：